Unexpected flashovers occurred at certain sections in the SBB overhead system, which caused electric arcs and protection trips. ENOTRAC performed a series of measurements together with SBB in order to understand the root cause of this, and to determine possible remedial measures.
The measurement results were compared with theoretical simulations. This led to understanding that flash over of load switches caused reflections at the end of conductors, where high overvoltage occurred. These overvoltages could exceed the insulation capability of some components. Possible measures against these effects can now be assessed because of this understanding.
ENOTRAC AG, Seefeldstrasse 8, 3600 Thun, Switzerland, Tel: +41 33 346 66 11, Fax +41 33 346 66 12
ENOTRAC SA, Avenue de la Gare 1, 1003 Lausanne, Switzerland, Tel: +41 33 346 66 19, Fax +41 33 346 66 12
ENOTRAC UK Ltd, Chancery House St Nicholas Way Sutton, Surrey SM1 1JB England, Tel: +44 20 8770 3501